The Reporter 4.0 is used for the remote signalling of short-circuits, earth faults and additional status reports from a medium voltage network. The information is transferred by ComPass B or ComPass B 2.0 in particular.
Voltage, current, load flow direction, power factor, power, energy and frequency are also measured and monitored. The received reports are transferred to iHost through a bidirectional data connection.
The Reporter 4.0 is housed in robust, weatherproof housing for wall mounting and can be configured using Windows-based PC software and iHost.
Reported short-circuits and earth faults are securely sent to SCADA via the iHost system and can be retrieved by any web-enabled device at any time. Notifications can also be received by e-mail and / or SMS.
- Detection and forwarding of digital states as generated e.g. by short-circuit or earth fault indicators, door contacts etc.
- Transfer via bidirectional data connection to iHost
- Auxiliary supply necessary
Automatic date and time synchronisation
Transmission of signal field strength
Fault and status notification via SMS and / or e-mail
16 digital inputs (hardware)
8 analogue inputs (4 – 20 mA) (hardware)
63 Modbus (digital) – 47 if hardware inputs are used
68 Modbus (analogue) – 60 if hardware inputs are used
Bidirectional data connection to iHost
|Internal power supply|
Back-up battery, max. 24 h
|External auxiliary supply||100 – 240 V AC (50 – 60 Hz)|
Glass fibre reinforced polyester, IP66
|Temperature range||-20 to +65 °C|